COMPLEX-MS-EMV cable glands ensure continuous contacting without gaps. The dome nut and the lamellar insert are simply pushed onto the lead. The exposed cable shield is folded around the lamellar insert, and the gland body is then pushed on. The screw-fitting of the dome nut ensures that the cable shield is pressed over a large surface between the torsion-protected lamellar insert and the gland body. The result is a very good metal contact area of the cable shield via the gland body to the housing protected from external environmental influences. The protection rating IP69K is confirmed for the sizes M12 to M25, M50 and M63.
COMPLEX-MS-EMV are to be installed as follows: Cut off outer cable sheath and expose braided screen over a length of approx. 10-15 mm, depending on the cable diameter. Push dome nut and lamellar insert with sealing ring onto the cable. Bend braided screen outwards at a right angle (90°). Fold braided screen towards outer sheath, i.e. by another 180°. Push gland body up to braided screen and turn briefly around both sides of the cable axis. Push lamellar insert with sealing ring into gland body and snap anti-redation element into place.
Firmly screw on dome nut.
Material: Brass, nickel-plated
Temperature range: -20°C to +100°C
Protection rating: IP 68 – 5 bar
Approvals: VDE, UL, CSA